By American Society of Heating
The 2008 ASHRAE guide - HVAC platforms and gear discusses a variety of platforms and the apparatus (components or assemblies) that include them, and describes beneficial properties and changes. this data is helping approach designers and operators in identifying and utilizing apparatus. it truly is divided into seven sections:
- Air-Conditioning and Heating platforms
- Air-Handling gear and parts
- Heating gear and elements
- Cooling gear and parts
- General elements
- Packaged, Unitary and Split-System gear
Read Online or Download 2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition) PDF
Similar ventilation & air conditioning books
In lots of climates constructions are not able to supply convenience stipulations for year-round occupancy with out the good thing about a heating method, and such a lot HVAC engineers will usually be concerned with concerns about the layout, install and function of such structures. additionally, in temperate climates, heating of constructions bills for a wide slice of annual carbon emissions.
“Tricks of the exchange” For state of the art HVAC layout on development Jobs of Any measurement! This totally revised, industry-standard instruction manual offers a wealth of HVAC layout details encompassing every kind of facilities―from workplaces and hospitals to advertisement areas and desktop rooms. Written in an overview structure for ease of use, this sensible reference deals enormous quantities of field-tested equations and ideas of thumb and lines all-new insurance of the newest development elements and fabrics.
ASCE/SEI usual 52-10 applies to fiberglass-reinforced plastic (FRP) stacks these stacks the place the first aiding shell is made up of FRP. layout of Fiberglass-Reinforced Plastic (FRP) Stacks outlines the issues that has to be made for either the mechanical and structural layout; emphasizes what attention has to be taken for wind- and seismic-induced vibrations; supplies instructions for ultraviolet safeguard and choice of fabrics; states the necessities for lighting fixtures and lightning safety dependent upon present construction and federal codes; supplies the necessities for hiking and entry established upon present Occupational protection and wellbeing and fitness management (OSHA) criteria; emphasizes the real components concerning fabrication and development; and descriptions components requiring upkeep and inspection following preliminary operation
Additional resources for 2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition)
This can vary from 18 in. to 5 ft and must be allowed for in the layout and dimensioning of the air-handling unit. Dehumidifiers For most routine applications, such as offices, residences, and schools, the air-handling unit’s cooling coil provides adequate dehumidification. Where a specialty application requires additional moisture removal, desiccant dehumidifiers are an available accessory. Dust can be a problem with solid desiccants, and lithium contamination is a concern with spray equipment.
AIR DISTRIBUTION Once air-handling system and air-handling equipment have been selected, air must be distributed to the zone(s) served. Ductwork should deliver conditioned air to each zone as directly, quietly, and economically as possible. Air distribution ductwork and terminal devices selected must be compatible or the system will either fail to operate effectively or incur high first, operating, and maintenance costs. Ductwork Design Chapter 35 of the 2005 ASHRAE Handbook—Fundamentals describes ductwork design in detail and gives several methods of sizing duct systems, including static regain, equal friction, and T-method.
If a constant-volume system is oversized, reheat cost becomes excessive. Fig. 9 Constant-Volume System with Reheat and Fan-Powered Terminal Unit Fig. 9 Constant-Volume System with Reheat Fig. 10 In commercial applications, use of a constant-volume reheat system is generally discouraged in favor of variable-volume or other systems. , for infection control). Variable Air Volume (VAV) A VAV system (Figure 10) controls temperature in a space by varying the quantity of supply air rather than varying the supply air temperature.
2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition) by American Society of Heating